Pressed steel sectional water tank constructed with hydraulically pressed flanged panels, conform to BS 1564: 1975 and SS 22: 1979
Flanges of Plates:
The tank plates are pressed with a combined double flange at an angle of 45 degree and 90 degree to the face of the plate on four sides.
Stays and Cleats:
The stays and cleats are made of steel angle bar and steel plate.
Bolts, Nuts and Washers:
Hot Dipped Galvanized steel bolts, nuts and washers for internal and external.
Nontoxic PVC foam to be used for all jointing between tank panel flanges.
Panel type tank cover supported by trusses and poles 600 x 600 square manhole and 100mm air-vent supplied as standard for each compartment.
Water Level Indicator:
Mechanical Ball Float Type.
Aluminum ladder for internal and external.
(a) Hot Dip Galvanized conform to BS 729 or ISO equivalent.
(b) Black Bituminous Coated.
Fire Tanks / Steel Sectional Tanks: